As per shown in the picture, the rag bolt must be grouted into the cement/concrete wall.
The bolts must be fixed to the cement/concrete wall.
Allow setting & checking than install it using nut and washer.
Measure tape, Keyhole or saber saw, Hammer, Glasses, Rags or Paper toweling, Drill (1/2 dia, drill bit or larger), Pencil, sealant, sharp knife or scissors.
Please Note : Please install it in a way that future removal from underneath the counter top is possible without damaging the counter top.
|ITEM||PROBLEM||PROBLEM REASONS||CORRECTIVE ACTIONS|
|Wash Basins / Table Top||1. Overflow Chocked And Foul Bed Odor||Waste Coupling Used May Be Full Threaded||Waste Coupling Should Be Changed To Slot Cut Coupling|
|2. Water Deposit On Tap Platform Area And Inside Bowl Area||Basin Is Not fixed in level or bracket is not in level||should be done by proper leveling|
|3. there is no tap hole in basin||tap hole could be semi punched from back side||tap hole should be created by plumber from semipunched area|
|Ewc / pan / anglo indian||1. Water not coming in bowl area while flushing||flush bend is not inserted up to the end of inlet hole||insert the flush pipe up to the end of inlet ( for pan closet) check whether flush pipe is not covering flush hole which is in both side of inlet wall|
|closet / pan may be not leveled||should be done by proper leveling|
|one piece closet||1. Water not coming in bowl area while flushing||mechanism inside tank could not working properly||change the centre pump of mechanism|
|there is no water in flush tank||increase the ball cock height to the max level|
|2. water is continuously leaking inside the bowl||mechanism inside tank could not working properly||change the centre pump of mechanism|
|3. water quantity insufficient for effective flushing||ball cock height adjusted at lower level||increase the ball cock height to the max level|
|4. uneven flow of water from both side of closet||closet is not leveled properly||closet should be in proper level|
|wallhung water closet||1. Water not coming in bowl area while flushing||flush valve may not working properly / concealed cistern is not working properly||should change flush valve / concealed cistern|
|flush pipe is not inserted up to the end of inlet hole||insert the flush pipe up to the end of inlet|
|2. water is continuously leaking inside the bowl||closet is not leveled properly||closet should be in proper level|
|3. water quantity insufficient for effective flushing||connection between closet outlet and drainage pipe is not proper||should be done by proper connection by experienced plumber|
|couple closet ( 2 pcs closet )||1. uneven flow of water from both side of closet bowl||both arm of driverter pipe not inserted equally in both side of the closet||both arm of driverter pipe should be inserted equally in both side of the closet|
|2. water is leaking between the cistern and closet||diverter pipe not fixed properly in the outlet of cistern||diverter pipe should be fixed properly in the outlet of cistern|
|rubber ring containing bolt is not tightened properly||rubber ring containing bolt should be tightened properly|